Retrotec 6112F Hi-Power Fire
To see if dampers really have the vent area they claim to have, they need to be tested and this model does that really well. It not only has lots of flow but can create 100s of Pa to see at what point the Pressure Relief Vents actually open.
Test for hold times in flooded volumes up to 51,000 cu ft (1000 m3) for Inert agents and 70,000 cu ft (2000 m3) for halocarbon chemical agents.
Testing pressure relief vents will require more power however. This system will test the venting for a volume up to a maximum of 12,000 cu ft (330 m3) for Inert agents although vents up to 8 sq ft (0.8 m2) can be measured individually.
Fan Model #: 6000 Flow Into: CFM litres/sec m3/h Free Air 8,100 3,823 13,762 Maximum Flow*, per fan 50 Pa 7,700 3,634 13,082 75 Pa 7,400 3,492 12,573 Minimum Flow: 50 Pa 9 4 15 -on Range B29 Dimensions: 26" × 25.5" × 9.5" (66 x 65 x 24 cm) Weight: 36.3 lb (16.5 kg) or 38 lb (17.2 kg) with Ring A & Plated B8 installed Flow Accuracy: +/-5% Power: 120V@60hz/22.0A or 240V@50hz/10.9A or 110V@50Hz/22.0A Recommended Fan Calibration Interval: 5 years Digital Gauge Model: DM32 WiFi Door Panel and Frame Model: AL250 Type of Panel: Regular Cloth Panel & Frame – Single 1000/3000/5000/6000 Fan Type of Frame: Regular Sized Red Anodized Frame Collapsed: 27 1/8” X 53 3/8” (68.9cm X 135.6cm) Expanded: 43 5/8” X 97 ½” (110.8cm X 247.6cm) Frame Thickness: 1.75” (5.3 cm) Weight: 16 lbs (7.3 kg)
* The max flow of the fan will vary depending on the following factors: Voltage, frequency, barometric pressure, back pressure, blade pitch, air temperature, bearing tightness, inlet air turbulence
* 5000/6000 series blower doors DO NOT work with the DM-2 digital gauge