Retrotec 6212F Lower Leak
The high power fans will test their ability to open and then accurately measure the entire relief vent pathway to ensure the peak pressure specifications are not exceeded.
Test for hold times in flooded volumes up to 102,000 cu ft (2000 m3) for Inert agents and 140,000 cu ft (4000 m3) for halocarbon chemical agents.
Testing pressure relief vents will require more power however. This system will test the venting for a volume up to a maximum of 24,000 cu ft (660 m3) for Inert agents although vents up to 16 sq ft (1.6 m2) can be measured individually.
Model 6000 Fan Flow Into: CFM Litres/sec M3/h Max Flow, per fan (60 Hz) Free Air 8,100 3,823 13,762 50 Pa 7,700 3,634 13,082 Reduces values by 15% for 50Hz fan 75 Pa 7,400 3,492 12,573 Minimum Flow: 50 Pa 9 4 15 on Range B29 Dimensions: 26" × 25.5" × 9.5" (66 x 65 x 24 cm) Weight: 36.3 lb (16.5 kg) or 38 lb (17.2 kg) with Ring A & Plated B8 installed Flow Accuracy: +/-5% Power: 120V@60hz/22.0A or 240V@50hz/10.9A or 110V@50Hz/22.0A Recommended Fan Calibration Interval: 5 years Digital Gauge Model: DM32 WiFi Door Panel and Frame Model: PN201 Type of Panel: Hard Panel - Single 1000/3000/5000/6000 Fan
* The max flow of the fan will vary depending on the following factors: Voltage, frequency, barometric pressure, back pressure, blade pitch, air temperature, bearing tightness, inlet air turbulence
* 5000/6000 series blower doors DO NOT work with the DM-2 digital gauge